System Sensor MCP5A-RP01-FG01 Flush Manual Call Point Fire Alarm Analogue Addressable
Unique 'plug and play' installation concept
Resettable plastic element option available (not included)
System Sensor Analogue Addressable Protocol Communications
Fully compliant with EN54 Part 11
This System Sensor Call Point Break Glass Unit MCP5A-RP01-FG01 is specifically designed to be used on System Sensor Fire Alarm Control Panels. The unit is designed to give a manual signal to the Sensor System Fire Alarm Control panel which will operate the fire alarm system.
These units are based on the industry standard KAC manual call point. They have been designed specifically to give installation efficiency, flexibility and compliance with the latest standards.
The System Sensor Manal Call Point Break Glass MCP5A-RP01-FG01 features an Integral LED. This LED will illuminate once the break glass unit has been operated. This feature allows easy identification as to which System Sensor Manual Call Point Break Glass has been operated.
The System Sensor Manual Call Point Break Glass Unit features a unique 'plug and play' concept that is designed specifically to reduce installation time by using a terminal block which can be wired during the initial installation cabling with a link to provide continuity for testing. During the commissioning phase, the links are removed and the terminal block is simply inserted into the connector at the back of the unit. No re-termination is required.
The System Sensor Manual Call Point Break Glass MCP5A-RP01-FG01 uses one of 99 possible addresses which is simply 'dialled in' using the two rotary decade switches on the rear of the unit.
A specialist test key may be inserted into the bottom of the unit to lower the glass and release the micro-switch and thus a full functional test is achieved.
The System Sensor Manual Call Point Break Glass unit is supplied as a flush mounting unit. It requires a single gang back box for surface mounting (not included).