Notifier Manual Call Point Break Glass Unit M700KACI-FG
- Manufacturer : Notifier
- Part Number : M700KAC-FG (Now Superseeded By M700KACI-FG)
- Addressable Call Point
- Supplied With Test / Reset Key
Notifier M700KAC-FG Manual Call Point
PLEASE NOTE : The M700KAC-FG unit has now been superseeded by the M700KACI-FG with integral isolator.
Notifier Manual Call Point Break Glass Unit M700KAC-FG
KEY FEATURES OF THE NOTIFIER MANUAL CALL POINT BREAK GLASS:
Unique 'plug and play' installation concept
Resettable plastic element option available (not included)
Notifier Analogue Addressable Protocol Communications
Fully compliant with EN54 Part 11
This Notifier Manual Call Point Break Glass Unit M700KAC-FG is specifically designed to be used on Notifier Protocol Fire Alarm Control Panels. The unit is designed to give a manual signal to the Notifier Fire Alarm Control panel which will operate the fire alarm system.
These units are based on the industry standard KAC manual call point. They have been designed specifically to give installation efficiency, flexibility and compliance with the latest standards.
The Notifier Manual Call Point Break Glass M700KAC-FG features an Integral LED. This LED will illuminate once the break glass unit has been operated. This feature allows easy identification as to which Notifier Manual Call Point Break Glass has been operated.
The Notifier Manual Call Point Break Glass Unit features a unique 'plug and play' concept that is designed specifically to reduce installation time by using a terminal block which can be wired during the initial installation cabling with a link to provide continuity for testing. During the commissioning phase, the links are removed and the terminal block is simply inserted into the connector at the back of the unit. No re-termination is required.
The Notifier Manual Call Point Break Glass M700KAC-FG uses one of 99 possible addresses which is simply 'dialled in' using the two rotary decade switches on the rear of the unit.
A specialist test key may be inserted into the bottom of the unit to lower the glass and release the micro-switch and thus a full functional test is achieved.
The Notifier Manual Call Point Break Glass unit is supplied as a flush mounting unit. It requires a single gang back box for surface mounting (not included).
Write Your Own Review